### Chain conveyor troubleshoot guide

Problem Identification & Corrective Action Sl No. Problem Potential Cause Solution 1 Chain rises off from sprocket 1.Excess chain slack. 2.Excess wear at the bases of sprocket teeth. 3.Excess chain extension. 4.Foreign material stuck to the bases of sprocket teeth. 5.Reverse rotation of conveyor 6.Uneven chain tightening of chain 1.Adjust the amount of slack equally at both sides. 2.Carryout hard facing of the sprockets 3.Replace the elongated chain parts. 4.Remove the foreign material from the bases of the teeth. 5.Avoid reverse rotation of the conveyor when chain tightened is uneven 2 Chain separates poorly from the sprocket. 1.Sprocket misalignment. 2.Excess chain slack. 3.Excess wear at the bases of sprocket teeth. 4.Uneven chain tightening of chain 1-Adjust alignment. 2-Adjust the amount of slack.

### Why thermal expansion is necessary in Boilers

Understanding the term expansion & contraction

When a body is heated it will expand & when it cooled it contracts. So body expands & deforms when heated & cooled. Change in temperature of a free body causes body to expand & contract without inducing stress. When the deformation of the body is restricted by means of any external force, there will be huge chances of stress induction. Such induced stresses are called temperature stresses. These may be tensile or compressive in nature.

Here L = Original length of the steel bar

∆t = Change in metal temperature deg C

É‘ = Coefficient of thermal expansion

Temperature strain e = Free deformation / Original length = ∆L / L

E = L É‘ ∆t / L = É‘ ∆t

Temperature stress Ïƒ= Young’s modulus X Strain = E X e

Temperature stress Ïƒ = E É‘ ∆t

Stress induced in a rigid or constrained body

P = Force exerted by a rigid support of constraint

We have Ïƒ = P / A

P = E É‘ ∆t A

Expansion in Boilers
Boiler is made up of plates, tubes, pipes and simple steel of various grades depending upon the duty conditions. Depending on the service such as cold air/hot air/cold flue gas/hot flue gas/cold water/hot water/saturated steam/super heated steam, thermal expansion movement of steel materials takes place to different extent in Boiler. Ignorance of thermal expansion movement of boiler components in design/installation may lead to failure of boiler components. The damage to boiler components can be costly affecting human life in some cases.
There are two types of expansions in Boilers

Absolute Expansion: Boiler whole mass expands.
Differential Expansion: Individual parts expansion. There are places where there is a relative expansion movement, which can cause stress in those parts.
In boilers expansion pointers are attached to all the pressure parts header to under stand the direction & value of expansion.
Expansion pointers are used for verifying the expansion movement of the boiler. These are attached to the drum ends/bottom or top header ends. When the boiler is under commissioning stage the expansion must be monitored. Depending on the anchor points in X-axis and Y-axis, the expansion is predicted by designers. The same is counter checked at site. Deviations in the form of non-uniform expansion should be checked.
Modern boilers expand towards bottom, during start ups & shutdown it is very important to observe the Boiler expansion.
Expansion of the metals depends on;
• Change in metal temperature
• Length & area of the materials
• Coefficient of expansion of the materials

Provisions for thermal expansions in boilers:

• Boilers all headers bottom space should be free from obstacles
• For air & flue gas ducts expansion bellows may be of metal or fabric should be provided
• Expansion loops for all steam lines should be provided
• Spring supports & hangers for steam line & hot water lines
• Rocker washers for steam drum & super heater headers supports
• Provision of stay bolts

• After shutdown, ensure all foreign material from Boilers & ductings have been removed completely
• Ensure all temporary supports & platforms have been removed from boilers & ducting
• Ensure there is no welding between any pressure part & hot ducts with platform or other or beams which can restrict the expansion
• Ensure steam line drains line are free to expand with steam lines
• Ensure there are no any uneven expansions

Examples:

A square rod of size 20mm X 20 mm in cross section & 2000 mm in length is allowed to expand by fixing both of its ends. Determine the force developed if the rod is heated from 25 degree c to 150 deg C.

L = 2000 mm
A =20 X 20 = 400 mm2
E = 2 X 105 Mpa
É‘  = 12 X 10-6 0C
∆t = 150-25 = 125 0C
We have             P = ÏƒA
P = E É‘ ∆t A
P =2 X 105 X 12 X 10-6 0C X 125 X 400 = 30000 N
Force developed at the end P = 30 KN

What is the expansion of Boiler side water wall panel , whose total length is 18 meters & metal temperature is 295 deg c. Consider atmosphere temperature 30 deg c &  É‘  = 12 X 10-6 0C
Expansion of side water wall panel ∆L =L É‘ ∆t = 18 X = 12 X 10-6  X (295-30) =0.068mm = 68mm

Restricted expansion in Boilers or steam lines will lead to..
• Damages to the restricted part
• Damage to the refractory & sealing
• Leakages
• Secondary failure
• Tube/pipe puncture
• Explosions

 Available @ Flipcart/Amazon/Notion press

Hi all,

### Boiler feed pumps (BFP) questions & answers for interview

Boiler feed pumps (BFP) questions & answers for interview: 1-What is the function of Boiler feed pumps (BFP) in power plant? Functions: To supply the feed water to boilers To conduct the Boiler hydraulic tests To supply the desuperheating & attemperator water required for process steam lines & boilers respectively TOP-6 BEST POWER PLANT O&M BOOKS Boiler calculations for Boiler operation engineer (BOE) exam Viva Questions & answers for preparation of BOE exam & interview  2- What are the type of prime movers (drives) used for BFPs? Prime movers: LT drive (415 V) HT drive (11 KV) Turbo drive (Steam driven) 3-What are the auxiliaries associated with BFP? BFP auxiliaries Cooling water pump & lines Lube oil system ARC valve Mechanical seal flushing system Balance leak off line & its PRV 4-What are the various pipe lines connected to BFP? Questions & Answers on AFBC Boilers Suction pipe line D

### Basic things you must know about nut bolts & spanners

A Bolt is a mechanical device which has head on one end of a body and a thread on the other end designed for fastening of two parts. Bolt is inserted into holes in assembly parts, it is mated with a tapped nut. Tension is normally induced in the bolt to compress the assembly by rotating the nut. This may also be done by rotation of the bolt head. A Screw is a headed and threaded bolt used without a nut. It is inserted into an internally tapped hole and tension is induced by rotation of the screw head. A Stud is a fastener with no head but it has threads at both ends of the shank. It, like a screw, has one end those screws into a tapped hole. A nut is used on the other end to create tension. Major diameter – largest diameter of thread (D) Minor diameter – smallest diameter of thread Pitch – distance between adjacent threads.       Boiler calculations for Boiler operation engineer (BOE) exam TOP-6 BEST POWER PLANT O&M BOOKS Types of nut bolts & Washer

### Calculation of heat rate & efficiency of the power plant

Heat rate  is the amount of energy used by an electrical generator/power plant to generate one kilo Watt-hour (kWh) of electricity Heat rate (HR) = Heat input / Power generation =Kcal / Kwh Boiler calculations for Boiler operation engineer (BOE) exam Viva Questions & answers for preparation of BOE exam & interview Total heat input: The chemical energy available in the fuel (coal, biomass, oil, gas etc) is converted into heat energy in Boilers, this process is called as oxidation. The heat available in the fuel is measured in terms of Kcal/kg, KJ/kg or BTU units. The part of this fuel is used as useful heat and rest is lost as dry flue gas loss, moisture loss, un  burnt loss, radiation/convection losses etc.Based on Boiler efficiency this heat energy from the fuel is utilised, generally fuel heat utilisation is in the range of 60 to 90%. This heat generated in the boilers due to oxidation of fuel is used to generate high pressure & temperature steam. Thus genera

### STEAM CONDENSER,VACUUM AND CALCULATIONS

A steam condenser is device or an appliance in which steam condenses and heat released by steam is absorbed by water. Heat is basically shell & tube type heat exchanger, where cooling water passes through tubes & steam condenses in shell. The functions of the condensers are: It condenses the steam exhausted from Turbine last stage Increase the thermal efficiency of the plant reducing the exhaust pressure and thereby reducing the exhaust temperature It maintains a very low back pressure on the exhaust side of the Turbine Supplies feed water to Boiler through deaerator TOP-6 BEST POWER PLANT O&M BOOKS Condenser related components: Hot well Cooling water inlet & outlet system Cooling tower Support springs or expansion neck Air Ejector system Condensate extraction system Cooling water tubes & tube sheet Vacuum breaker valve Safety valve or rapture disc Water box Air & water vent lines Types of steam condensers: Surface Co

### 22-Most likely Question Answer Guide for Boilers troubleshooting

TOP-6 BEST POWER PLANT O&M BOOKS 1.What are the emergencies that are expected to happen in boiler operation? Emergencies that can happen in boilers operation are: Boilers tubes leakage Failure of feed water control station Unbalanced draft in furnace Furnace explosion Blow down valve failure Feed water pumps failure Secondary combustion in super heaters and ESP Also read 16-Perfect reasons for increasing the fuel consumption of Boilers 2.List out the potential reasons for boiler tubes failure. Reasons for boiler tubes failure: Failure due to overheating Failure due to internal scales Failure due to aging Failure due to uneven expansion Failure due to ash and flue gas erosion Failure due to material defects Failure due to internal and external tube corrosion Improper or effected circulation due to opening/passing of low point drains 3.List down the sequential action taken after boiler tube leakage to restore the boiler. Following activities ar

### Questions answers & calculation on Boiler draught & Chimney

1-What do you mean by the term draught? It is the pressure difference, which causes flow of gases to take places. 2-What is the function of draught in Boiler? To supply the combustion air required for proper combustion To evacuate the combustion products from the furnace or combustion chamber To evacuate the combustion products to the atmosphere So draught is the pressure difference between the inside the boiler and outside air. Inside the boiler pressure is due to combustion products (Flue gas) & outside pressure is due to fresh atmospheric air. 3-What are the different types of draughts used in power plant boilers? There are mainly two types of draughts. Natural draught & artificial draught Natural draught is generally obtained by Chimney Artificial draughts have main two types Steam jet: It is again classified into Induced & forced draught Mechanical draught: This is classified into Induced draught, forced draught & Natural draught

### Boiler calculations for Boiler operation Engineer Exam (BOE)

1-Oxygen percentage in Boiler outlet flue gas is 4.9%, then what will be the percentage of excess air? We have excess air EA = O2 X 100 / (21-O2)                                    EA = 4.7 X 100 / (20-4.7)                                    EA = 30.71% 2-Calculate the Oxygen level (O2) in flue gas, if excess air is 25% We have Excess air EA = O2 X 100 / (21-O2)                                    25 = O2 X 100 / (21-O2)                                    O2 = 4.2% 3-A Boiler’s combustion system requires 5.5 kg of air for burning 1 kg of fuel, then calculate the total air required for complete combustion if its flue gas has 4.1% of O2 We have, Total air = (1 + EA/100) X Theoretical air EA = O2 X 100 / (21-O2) EA = 4.1 X 100 / (20-4.1) = 25.78% Therefore Total air = (1 + 25.78/100) X 5.5 = 6.92 kg of air per kg of fuel burnt 4-A Coal fired boiler having total heating surface area 5200 M2 produces 18 kg of steam per square meter per hour of heating surface, then calculate the Boiler cap